The repository administrator has not yet configured an RDF license.
IMPLEMENTSI RANGKAIAN PENGHITUNG KERAPATAN FLUKS NEUTRON TERKOREKSI N16 RSG-GAS BERBASIS LABVIEW
IMPLEMENTSI RANGKAIAN PENGHITUNG KERAPATAN FLUKS NEUTRON TERKOREKSI N16 RSG-GAS BERBASIS LABVIEW Telah dilakukan penghitungan sinyal N16 terkoreksi (ϕN16-corr) untuk mendeteksi kecelakaan reaktifitas daerah daya. Penghitungan sinyal ϕN16-corr melibatkan dua kanal pengukuran, yaitu detektor kerapatan fluks neutron dan detektor laju dosis gamma. Rangkaian penghitung ϕN16-corr terdiri dari trigger amplifier (K), integrator (I), dan summing element (S). Rangkaian penghitung ϕN16-corr di simulasikan menggunakan program LabVIEW. Nilai histerisis yang didapatkan yaitu sebesar 0.01 V, dengan nilai batas 0.94 V dan nilai korreksi = -0.94 mV/s. Nilai selisih antara N16 terkoreksi modul perangkat keras terpasang dengan perangkat lunak adalah sebesar 0.04898 V. Kata kunci : Detektor kerapatan fluks neutron, detektor laju dosis gamma, LabVIEW, scram, sinyal N16 terkoreksi (ϕN16-corr). THE COUNTING CIRCUIT OF IMPLEMENTATION NEUTRON FLUX DENSITY CORRECTED N16 RSG GAS BASED LABVIEW The counting of the corrected N16 signal for detecting the reactivity a power reactor accident has been done. N16-corr signal calculation involves two measurement channels, namely detector of neutron flux density and the detector of gamma dose rate. The series of counters for φN16-corr consists of trigger amplifier (K), integrator (I), and a summing element (S). The series of counter φN16-corr simulated using LabVIEW program.Hysteresis value obtained is equal to 0.01 V, with a limit value of 0.94 V and the correction value = -9.4 mV/s. Corrected value of the difference between the N16 hardware modules installed with softwere is equal to 0.04898 V. Keywords: Detector ofneutron flux density, detector of gamma dose rate, LabVIEW, scram, N16 corrected signal (φN16-corr).
IMPLEMENTSI RANGKAIAN PENGHITUNG KERAPATAN FLUKS NEUTRON TERKOREKSI N16 RSG-GAS BERBASIS LABVIEW (File PDF)
IMPLEMENTSI RANGKAIAN PENGHITUNG KERAPATAN FLUKS NEUTRON TERKOREKSI N16 RSG-GAS BERBASIS LABVIEW (Other)
HTML Summary of #16363 IMPLEMENTSI RANGKAIAN PENGHITUNG KERAPATAN FLUKS NEUTRON TERKOREKSI N16 RSG-GAS BERBASIS LABVIEW